Junction boxes are metal or plastic enclosures used as housings for wiring connections. The connections within are called branch circuits and usually represent the end of a conduit run. Junction boxes make wire access easy, since all one must do is remove the covering to make alterations, repairs, or additions to a conduit. Junction boxes also protect wiring from the elements or environment, which can sometimes be corrosive or otherwise harmful to wiring material. Finally, junction boxes protect wiring from unwanted tampering, whether malicious or unintentional.
Junction Box Wiring Basics
Essentially, a junction box houses wire connections in order to split off power from a single source to multiple outlets. For instance, a distribution box might contain one wire power source that is connected through multiple wires to power several different lights.
Junction boxes are usually between 2 ½ to 3 ½ inches long and made of metal or hard plastic. The functional difference between plastic and metal depends whether or not the junction box is supposed to support any weight. Some metal junction boxes can support light fixtures; plastic junction boxes cannot withstand this weight. Additional differences include installation, in that plastic junction boxes are typically quicker and easier to install than metal ones. However, a standard junction box designed to simple cover wire splices can be either metal or plastic.
Wire Splices in Junction Boxes
All wire splices must be contained within a junction box for a building to meet electric code, although sometimes splices are missed and may present hazards as a result. Any exposed wiring can be dangerous, but exposed wire splices are especially prone to accident because they can be tripped over, expel sparks or misrepresent themselves be misperceived as playthings by children or pets. IP65 junction box are helpful for wire splices because they also allow one to easily locate the wire splice area.
Shut off the Power and Test the Wires
Turn off the power to the circuit you'll be working on by switching off the appropriate circuit breaker in your home's service panel (circuit breaker box). Test all of the wires you'll be working on with a non-contact voltage tester. The test should confirm that no voltage is present in any of the wires.
Remove a Knockout (Metal Box Only)
If you're using a metal box, remove a knockout on the box for each cable that will enter the box. Use a screwdriver and hammer to break out each knockout (metal disc), then twist off the metal knockout disk with pliers.
Mount the Box
Separate the circuit wires at the existing splice and loosen the cables as needed to make room for the new junction box. Anchor the box to the framing (or other support structure) with screws driven through the factory-made holes in the back or side of the box, as applicable.
Set up Clamps for Each Cable
Install a cable clamp for each cable, as needed. Standard plastic electrical junction boxes do not have knockouts and contain internal cable clamps. Metal boxes usually have internal clamps; if yours does not, install a locknut-type clamp for each cable. Insert the threaded end of the clamp through a knockout hole and secure the clamp inside the box with the ring-shaped nut. Tighten the nut with pliers.
This ad has no reviews yet. Be the first to leave a review.